Pisgah Forest, NC Heating & Cooling
Comfort Central is Pisgah Forest’s Top Choice for HVAC Solutions
Living in Pisgah Forest, we get the best of both worlds — warm southern summers and cool mountain winters. However, when the weather turns extreme, you want to be able to heat and cool your home so that you stay nice and comfortable.
The cost to have your HVAC system replaced usually ranges from $5,000-$10,000, with most people paying an average of $7,000. However, the cost for HVAC replacement services can be significantly higher or lower depending on a number of factors including the size of the units you’re having installed, the brand and the SEER rating of the units and the labor costs.
Comfort Central offers fast and reliable HVAC replacement services. To have your HVAC systems replaced, give us a call today.
Finding a good HVAC contractor can make all the difference when it comes to your HVAC systems. Some of the ways you can find a quality HVAC contractor include:
- Asking for HVAC contractor recommendations from friends and family.
- Searching online for HVAC contractors in your area.
- Making sure they’re certified.
- Reading through their reviews and ratings.
Comfort Central’s technicians are certified and are experts in the HVAC field. If you’d like to find out more about the HVAC services we offer, give us a call today.
If your HVAC systems aren’t working properly, there are a few things you can do to try to fix the problem yourself before calling an HVAC technician. Some quick fixes include:
- Checking the air filters.
- Making sure the thermostat is set correctly.
- Replacing the thermostat’s batteries.
- Clear the area around your units.
If you’ve tried these fixes and your HVAC systems are still having problems, the experts at Comfort Central can help. Give us a call for more information on our HVAC repair services today.
for Pisgah Forest, NC
Our Reviews by City
Bob - Pisgah Forest, NC 28768
Over the past year and a half, Comfort Central installed a new AC unit and furnace for us and modified the ducting for our remodeling project. Everyone at Comfort Central has been on time, courteous and professional. Kevin has been extremely helpful in working through challenges on our remodeling project. The team went beyond expectations to help install our new cooktop hood. I will use Comfort Central again.
Knowledgeable and great service.
Blake - Pisgah Forest, NC 28768
Hands down the best HVAC tech !
Chris - Pisgah Forest, NC 28768
Cameron is by far the best technician we have met in both customer service skills and technical knowledge. He went above and beyond and answered all of our questions. We have the utmost respect and confidence in him. We would recommend him and the company without hesitation. Thank you for coming out on such short notice as well!
Great work, as always!
Jeff - Pisgah Forest, NC 28768
We know we can always depend on Cameron and the Comfort Central team whether we have a system emergency or we need routine maintenance.
Elizabeth - Pisgah Forest, NC 28768
Great communication, polite, excellent work, cleaned up and answered all questions.
Zoe - Pisgah Forest, NC 28768
Always provides timely, courteous, and efficient service. Cameron is the best!
Dianne - Pisgah Forest, NC 28768
Once again Cameron arrived on time to service our HVAC system. Cameron is so nice and his work ethic is superb. He is a great representative of the company and the reason we continue to use Comfort Central for our HVAC needs.
Rick - Pisgah Forest, NC 28768
Technician always efficient and friendly.
Russell - Pisgah Forest, NC 28768
always great service
Performed cooling tune up on system cleaning all components, treating and flushing drain line, cycling system to check operation including electrical, refrigerant balance, start up, operation, shutdown. Ran system in both heat and cooling. Everything looks and runs great! No recommended changes at this time.
System condensate pump outlet failed probably in recent power outage and must be replaced will return with outlet so condensate pump doesn't have to be on an extension cord
Replacement of Evaporator Coil under Manufacturer's Warranty Parts Warranty. Includes Warranty Processing. Manufacturer's Shipping and Handling are a separate line item.
Remove and replace 6’ of trunk duct to the left side of air handler with 10” x 20” metal duct and transition into existing duct. Fabricate and install a 6” x 14” duct to go into addition where we will add (2) ducts. One to supply the addition and 1 that will be capped off for future use. Vent the new 390 cfm kitchen exhaust hood. The roof termination will be installed by others. September 8th Added bigger trunk line section. Connected new duct to section. Hung and connected stove vent
Tested power at outlet and voltage with zero. Looked around the house for a GFI that might be tripped, didn't find any GFIs but customer and I found that outdoor outlets did not have power. It's a possibility that the outlet is tied in on that circuit. Recommend customer calls an electrician to find out why they are missing voltage.
Tstat is no nonresponsive. Jumped wires at tstat system started no issues. Need to replace tstat on upstairs system Replace programmed and tested new tstat
Swapped out heat kit and breaker in panel. Tested heat kit using damper board. System running normally.
Adjusted refrigerant balance from yesterday's condenser coil install. Indoor temperature was high during charging which skewed refrigerant charge parameters. Added 2.5 lbs r410a cycling to check operation. System now has a 20.5°F temperature differential and is cycling normally.
Replacement of condenser coil under warranty after replaced coil and did triple evacuation charged system to manufacturers specs and cycled system to check operation. Everything running within manufacturer's specifications.
Performed cooling tune up on heat pump system checking all electrical, refrigerant balance, cleaning of indoor and outdoor coils and flushing and treatment of drain lines. Changed filter today 8/22/23. Did not identify a single source for the cause of smell coming from crawlspace. Believe could be caused by soil gas build up underneath the crawlspace wrap. Would recommend soil gas remediation to help alleviate the smell.
Found system communications wire connection had failed. Repaired connection and everything had come on normally. System cycles on and off normally no additional repairs needed at this time.
Performed ultimate cooling tune ups checking all electrical components, refrigerant balance, start up, operation, shut down. Cleaned indoor and outdoor coils. Treated drain lines and flushed with a light cleaner. Everything looks and runs great!
Added 1.5 lbs r410a and performed a leak search checking indoor and outdoor coils and lineset inbetween the two units. Checked every fitting and penetration on unit for leaks. Did not return any results with electronic leak detector. Performed a second sweep to verify results. Checked system operation after leak check to verify system is cooling correctly. Adjusted refrigerant balancing to align with manufacturers specifications.
Performed tune up on heat pump system checking all electrical components, refrigerant balance, cleaning of indoor and outdoor coils amd drains. Checking start up, operation, and shut down of system. Everything looks and runs great! No recommended changes at this time.
SEER2 20; HSPF2 9.5; EER2 13 Make: Bosch Model: BOVA36HDN1M20G Outdoor Unit BVA24WN1-M20 Air Handler 10 KW Electric Heat Honeywell HZ432 Zone Control Kit 16x8 Zone Damper 12x8 Zone Damper 8” zone damper (2) t-6 Thermostats (1) wireless thermostat kit Tech Pure Merv 11 Media Filter Installation shall include: Equipment specified above plus materials and labor to include: • We will install system using zone dampers in existing duct work and adding a zone for basement room. Basement room will not get a vote to turn on the equipment. • Upgrade to electrical panel is not included. • Permit Fee for Installation. • All work will be completed in a professional workmanlike manner. • Old equipment and trash from installation will be removed from premises. • Bosch Manufacturer’s Warranty: Ten (10) Year Limited Parts, including Compressor. • Honeywell warranty: five (5) years parts. • One (1) Year Labor Warranty Provided
Found compressor drawing locked rotor amps. Will need replacement. Has 3/4x 3/8. Line set. Unit is 15-1/2" wide. R-22 1-1/2 ton system.
Replaced evaporate coil add 4 lbs 410a
Provide Materials and Labor for replacement of Condensing Unit, under Manufacturer's Service Bulletin TB14-101RA.
Performed Ac cooling tune up checking electrical, refrigerant balance, unit start up operation shut down. Cleaning of indoor and outdoor coils and drains.
Charged system with 3 lbs 5 oz of 410a. System had a 20 degree delta after charge.
Found t Stat sub base making a convex shape not allowing Stat to sit correctly against the wall. Reset t Stat sub base and cycled system to check thermostat operation
GOODMAN AIR CONDITIONER - Found capacitor flat replaced capacitor and cycled unit to check operation Found unit condenser fan motor has open windings on common causing fan not to come on, found condenser fan blade fused to motor shaft. Replaced condenser fan motor, fan blade, and capacitor and cycled to check operation. Everything running within manufacturer's specifications.
Found generator add on for unit not allowing sustenance to have power noise generator recommend electrician repair generator connection
Found system low on r410a refrigerant added 3.5 lbs of refrigerant and cycled to check unit operation
Replaced t Stat with white Rodgers programmable t Stat and cycled system to check operation. Also wants a quote to duct in dehumidifier to main system.