Heating & Air Conditioning Services in Fairview, NC
Trust Comfort Central With Your HVAC Service Needs
For exceptional heating, air conditioning and indoor air quality services in Fairview, NC, call Comfort Central, Inc. Our professional, extensively trained HVAC service technicians have all the knowledge and experience necessary to ensure your home is kept comfortable throughout the entire year.
The first thing you should do is inspect the outside unit, clean the area, and get rid of any weeds or debris that are obstructing airflow.
Next, make sure your filter is clean by checking it. When the airflow to the evaporator coil is restricted by a dirty filter, the coil frequently freezes. You might need to change your filter more frequently if you have pets or use your air conditioner frequently. Take your filter out and see if you can see through it as a good test.
You should call a professional if your air conditioner is still not cooling the air. You may have a problem with your compressor or refrigerant.
The national average for replacing an entire HVAC system is $7,000, and costs can range from $5,000 to $10,000. This equals between $25 and $60 per square foot. The size and brand of the HVAC system, the size of the house, the length of the ductwork, and the efficiency rating of the new unit all affect prices.
Increasing the ventilation in your home is one option. In order to improve air circulation and reduce the amount of harmful particles in your home, ventilation involves bringing in fresh air from the outside. If the weather permits, it's a good idea to open the windows. Additionally, you can use window fans to push potentially hazardous air out and draw fresh air in.
Another option is to think about purchasing a portable air purifier with a HEPA filter, which can capture and eliminate minute airborne particles like pollen, smoke, bacteria, mold, and dust. Although the cost of air cleaners varies greatly, some models that cost around $100 can effectively clean a room.
From complete installations to system maintenance and repair services, our experienced and fully certified service technicians are qualified to handle any service that you may need. Your comfort is our business, and your satisfaction our guarantee!
for Fairview, NC
Our Reviews by City
Mary - Fairview, NC 28730
Mark - Fairview, NC 28730
cameron has been very helpful and informative.FairviewNC28730 35.5225-82.3075
Mary - Fairview, NC 28730
Myrtle - Fairview, NC 28730
Friendly and efficientFairviewNC28730 35.5325-82.3875
excellent company with exceptional customer service
Marsha - Fairview, NC 28730
I have been dealing with Comfort Central for many years. They do excellent work they show up on time I trust them to take care of all of my HVAC needs. they may be more expensive than other companies, but you get what you pay for.FairviewNC28730 35.5175-82.415
Comfort Central provides great service.
Marilyn - Fairview, NC 28730
Comfort Central is an excellent company. They have provided expert maintenance on the mini split system we purchased from them.FairviewNC28730 35.515-82.395
Quick appointment n service
Scott - Fairview, NC 28730-9642
Delivery person told homeowner it was cold in garage apartment. On arrival system is blowing hot air as intended. Conclusion: delivery driver mistook defrost cycle as a malfunctioning unit.
Delta T of 23-25 on all power heads. Treated all coils indoor and outdoor with green coil cleaner. No signs of over-amping from outdoor unit. Blowers are all clean from the previous pull and clean visit. Filters have very light dust. No signs of water leakage from any of the power heads. Defrost functioning normally. System is heating normally.
Delta T of 33. Filter changed. Drain trap brushed out. Checked coils, blowers, amps, temps, and pressures. Treated outdoor coil with coil cleaner. Instructed homeowner on using the automatic setting on her upstairs thermostat. Patched test hole. Tested heat strip. System is functioning normally.
Need to return.
Performed ultimate heating tune up checking all furnace components, performed full combustion analysis, cleaned burned and flame sensor, checked all electrical, checked furnace start up, operation, shut down, exercised safeties to insure proper unit operation. Everything looks and runs great! No recommended changes at this time.
Thermostat subbase was convex on wall causing thermostat to disconnect from EIM and shut off dehumidifier. Reseated subbase, shimmed behind it and made sure sits flat against the wall. Adjusted dehumidifier to make sure runs efficiently - system achieved 45% humidity in 15 minutes. Flushed drains cleaned float switches to insure no drainage issues. Everything else looks and runs great! Covered under workmanship and satisfaction guarantee.
Delta T of 16. Subcool of 11. Superheat of 3. Filter needs to be replaced. Blew out trap to condensate pump. Treated outdoor coil with cleaner. System is old (r22). Recommended new unit. Homeowner requested estimate.
Performed 3 ac tune up services checking all electrical components, refrigerant balance, unit start up, operation, shut down. Cleaning of indoor and outdoor coils and drains. Everything looks and runs great no recommended changes at this time.
Recommend replacement of right side of house system. Will return to give an estimate to replace system.
Ac tuneup. I think The rattling noise was coming from a register. I made an adjustment to it started and stopped the unit three times I couldn’t hear another rattle.
Tune up on all heads, air handlers and out door units . No issues Dehumidifier in art room was not working. Cycled off and on. System started working. Call tech-support they recommend we replace the internal board and user interface board. They estimate 10 days until parts arrive.Being that there was a call for Dehumidification in the master bedroom And the dehumidifier was not working. The air handler blower was still running. This would cause over cooling and humidity being that if another Device on that system was running would make the coil in the original air handler cold and wet from condensation. Once the dehumidifier parts are changed the warm air that comes out of the dehumidifier will warm the air going across the cold coil therefore no longer getting over cold and it will remove the humidity on that coil as it runs.
Found attic system drain had backed up causing unit float switch to trigger to turn system off. System working upon arrival because emergency drain pan had lost enough water to allow unit to come on. Checked operation of system. Removed drain blockage. Sold 3 tune ups for August 17th 10am time slot.
Deep Cleaning of (4) Indoor Power Heads and Replacement of PC Communication Board in outdoor unit. Will return with 2 indoor power boards for right side Mitsubishis
AC NO COOL - MITSUBISHI UNIT No power At thermostats of zones.. found the moisture sensor in emergency drain pan to be tripped causing a lockout. Reset switch tested operation. Did not find any type of moisture in drain pan. It’s possible the water sensor switch could be going bad if this happens again I recommend we replace the switch
Found outdoor p.c. control board has failed. Recommend replacement will also quote deep cleaning of 4 indoor units. Also wants quote for adding an additional unit
Delta t of 18-24 across all units. Washed filters for indoor power heads. Filter in attic unit still good. Checked amps, caps, temps, and pressures. Treated coils with green cleaner. Systems functioning normally.
Delta T of 21. Filter cleaned. Fixed insulation on blower door that came loose. Checked temps, pressures, caps, and amps. Blower clean. Coils clean. Treated outdoor coil with green cleaner. System is functioning normally.
Performed Ultimate Cooling Tune-Up on Daikin Mini-split system in Fairview
Fix the clog drain and didn't air-conditioning tuneup on a goodman heat pump
Ductless heat pump tune up.